Notice: All the products in our website are the material object photographies,taken in our factory real
product.Also,in order to ensure the quality,in China,all the products are direct selling from our factory.
Recently,some illicit competition companies copy the photos from our website,and made it in small scale
factory in domestic premises,the poor quality product is very dangerous,seriously done harm to consumers'benefit,Please pay attention.
What is this heat exchanegr work Condition? 1)Refrigerant side (Between the tube and shell):R22,R134a,R404a,R407c,R410a,R600a,etc.
Max working pressure is 50 Bar.
2)Water side (inside of the tube):Domestic water,tap water,antifreeze (glycol solution)
Max working pressure is 32 Bar.
3)This structure A suitable for used as condenser,for heat mode.
It's widely used in air-source heat pump and water-source heat pump.
What are the Materials? 1)Heat transfer Tube:High efficiency finned copper tube,(Optional: finned nickel-copper tube or finned double-wall copper tube)
2)Shell: High quality steel ,thickness:4mm.
3)All the material are ROHS conformance.
Which are the good features of this heat exchanger? 1)Thanks to the small flow rate, big temperature difference design,easy to get the high-efficiency heat transfer ability.
2)Small volume Compactly design is helpful to save the space ,Thus reduce the size of whole units. 3)Best welding procedure and inspect all the welding line with high technology methods--Ultrasonic and halogen gas test,make sure strong and not leak,have the CE-PED certification.
How to get the high effciency of this heat exchanger? 1)Use efficiency finned copper tube, heat exchange area is 3.7 times than the Smooth Tube,it is a important cause of high efficiency. 2)Inside the tube is screw thread,so the water will eddy flow forward ,it's another cause of high efficiency. 3)The compact helix structure of the coil ensures sufficient heat exchange between the gas and water.
What about the Safety? 1)Whole tube inside shell has no internal joint,that means no welding bug. 2)The Copper Tube is fully shaped and then installed into the shell thus free from Products processing defects.
3)The shell was welding by argon arc welding,we inspect the welding line with Ultrasonic leak detector in the first.and then we test the refrigerant system with 50 Bar halogen gas again,make sure strong and not leak. Have the CE-PED certification.
4)There is no block on water loop and the water flow is smooth,thus keep it avoid dirty.Also,the water pipe is on the lowest position ,and easy for drainage in cold season,avoid freeze.
What are the detail dimension and parameters ?
Please check out the detail parameter from the following list.---Model: GAH04-CMF